You are here:front page » Charging pile installation and power-on process
Charging pile installation and power-on process
1. Unpacking and inspection
After unpacking, first check whether the device is scratched, dented, or damaged; then check whether the accessories are complete, and pay special attention to the fact that the power module is packaged in a separate carton.
2. Installation conditions
The installation ground of the equipment should be flat and hardened, and fixed by four expansion screws at the bottom. It should not be installed in low-lying places to avoid water accumulation. The equipment cannot be installed in a confined space, good ventilation and heat dissipation must be ensured, and a maintenance space should be reserved around the door.
3. Module installation
Open the front door, release the side door latch, insert the power module into the left door latch slot, pay attention to the installation direction, do not use excessive force, and fasten the fixing screws after inserting it in place.If the installation fails after several attempts, you need to open the right door to fine-tune the rear terminals of the power module.
After all the power modules are inserted in place, you need to dial the code according to the corresponding stickers M1, M2.... The dialing rules are shown in the figure below (taking 60kW dual guns as an example):
Detailed introduction of charging pile module dial code
Please click the menu: " Product Service "---" Technical Service "--- " Module Dial"
4. Cable access
Cable production and connection requires professionals to operate the equipment. Cable access must be in accordance with the three-phase five-wire (A, B, C, N, PE) standard, special tools are required for terminal crimping, and the connection screws must be tightened.
When inserting the power module, apply moderate force to avoid damage to the module terminals. The power module needs to be dialed before it can be used normally.